Accepta Dechlor is a high quality sodium thiosulphate based de-chlorinator product used for reducing or neutralising residual chlorine reserves following clean and chlorination procedures.
Accepta Dechlor can be used for post cleaning/chlorination procedures and other applications where residual chlorine levels are required to be reduced or eliminated to allow discharge to foul drain or natural watercourses.
Accepta Dechlor can also be used to dechlorinate water used in aquarium and swimming pools.
- High quality sodium thiosulphate.
- Rapidly reduces/neutralises chlorine levels post cleaning/chlorination procedures.
- Easy to use.
Application & Dosage Information
DECHLORINATION OF TANKS
Where it is necessary to remove the excess chlorine from a volume of water prior to discharge to sewer, this can be achieved using Dechlor
The Accepta Dechlor should be added at the rate of 11ml per ppm of Chlorine per m3 of water.
Example To remove 30 ppm of free residual chlorine in a 80m3 tank requires:-
11(ml) x 30(ppm) x 80(m3)
= 26,400 ml or
= 26.4 litres of Dechlor
N.B. It is important not to over dechlorinate since this will absorb any free chlorine residual in the incoming main.
Can be used for the dechlorination of cooling towers during cleaning.
When using Activ-Ox foam cleaning products drain the tower sump and fill with 2 inches of clean water and add the following cocktail of chemicals to neutraise the foam as ti drips into the sump.
-Approx 500ml/m3 of Accepta 2315 Defoamer
-Approx 500ml/m3 of Accepta Dechlor