Boiler Water Solid Condensate Treatment
Accepta 6309 is a solid form oxygen scavenger amine product containing DEHA.
This is a proprietary compound of diethylhydroxylamine (DEHA) which is designed to remove dissolved oxygen from the systems, while providing metal passivation.
As a volatile organic it will also protect the steam distribution system from oxygen corrosion. In the presence of heat, a portion of the product will break down to form neutralizing amines that will help elevate pH in the condensate system, protecting it from carbonic acid attack. This may reduce or eliminate the need for additional neutralizing amine. DEHA does not add dissolved solids to the system.
HOW MUCH TO USE
Feed 6 ppm of product to the feedwater per ppm of oxygen in the feedwater.
|Testing Method||In Feedwater|
|DEHA||> 0.1 ppm|
|Testing Method||In Condensate Return|
|pH||7.0 – 8.5|
|Iron||< 1 ppm|
Appearance: Solid – White
Odour: characteristic – amine
pH: ~11.5 @ 4%
HANDLING AND STORAGE
Accepta 6309 should be kept away from acids and oxidising agents in a cool dry area. Properly stored, the product will remain effective for 12 – 18 months. Consult Safety Data Sheet for further information
Accepta 6309 is available in
- 5.45 kilo containers (4 to a case)
Feed Accepta 6309 using an Accepta board system.
Available in three types:
- Gravity Fed – No pump needed, requires controller relay or timer
- Electronic Level Control – Pump needed
- Mechanical – Pump needed
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
For further technical assistance concerning Accepta 6309 please contact Accepta.
Safety, Storage & Handling
For full details concerning safety precautions, storage and handling procedures for this product please refer to the latest Safety Data Sheet.
To request the latest MSDS for this product please fill out the form below.