Kintec 2199 is a high-performance boiler water oxygen scavenger based on a blend of natural organic compounds which offer both corrosion inhibition and superior dispersive properties over conventional tannin treatments.
Corrosion inhibition is achieved via the dual ability of the selected compounds to act as an oxygen scavenger plus the supportive benefit of forming a protective film on the metal surface.
Kintec 2199 can also aid in magnetite film formation in the boiler.
Kintec 2199 contains a special blend to improve shelf life and prevent biological growth or spoilage of stored chemical.
- High-performance oxygen scavenger giving outstanding protection from oxygen corrosion
- Based on blend of natural organic compounds
- Excellent dispersive properties
- Aids in magnetite film formation in the boiler
- Convenient liquid product
|Specific Gravity:||1.07 – 1.12|
|pH:||5.0 – 6.0|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
Total The target dosage range for Accepta 2603 is 55ppm of product / ppm of 02 with a residual level of 400 – 600 ppm in the boiler water.
Kintec 2199 should be diluted no more than twenty times using softened or demineralised water (or condensate) and is dosed using either a metering pump (preferred) or a pot feeder, as appropriate.
Kintec 2199 is normally controlled within set limits in the boiler water. The specific limits will be determined by operating conditions and water quality.
Appropriate use of Kintec 2199 following the above dosing strategy will result in oxygen removal in the boiler water.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
Testing and Control
Kintec 2199 – Test using tannin, colourimetric or pocket colourimeter both available from Accepta.
Material of Compatibility
Safety, Storage & Handling
Kintec 2199 is a mildly acidic solution. Avoid contact with skin, eyes or clothing. If skin comes into contact with this product, wash with water. If eyes are affected, flush with water for at least 15 minutes and get medical attention.
For full details concerning safety precautions, storage and handling procedures for this product please refer to the latest Safety Data Sheet.
To request the latest MSDS for this product please fill out the form below.