Boiler Water Condensate Treatment
Accepta 6310 is a proprietary compound of blended amines (Morpholine & Cylcohexylamine & DEHA corrosion inhibitor) designed to minimise corrosion in condensate lines by balancing pH.
Product CANNOT be used in steam that will be in contact with milk and milk products.
HOW MUCH TO USE
Feedrate is dependent upon amount of condensate return and feedwater alkalinity and the amount of oxygen in the condensate. This product should be fed to the boiler or the feedwater.
|Testing Method||In Condensate Return|
|pH||7.0 – 8.5|
|Iron||< 1 ppm|
Appearance: Solid – White
Odour: characteristic – amine
pH: ~11.5 @ 4%
HANDLING AND STORAGE
Accepta 6310 should be kept away from acids and oxidising agents in a cool dry area. Properly stored, the product will remain effective for 12 – 18 months. Consult Safety Data Sheet for further information
Accepta 6310 is available in 4.0 kilo containers (4 to a case).
Feed Accepta 6310 using an Accepta board system.
Available in three types:
- Gravity Fed – No pump needed, requires controller relay or timer
- Electronic Level Control – Pump needed
- Mechanical – Pump needed
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
For further technical assistance concerning Accepta 6310 please contact Accepta.