Accepta 6058 is a high performance, highly concentrated nitrite based multi-functional solid chemical boiler water treatment product scientifically formulated for the treatment and protection of low pressure steam boilers.
Accepta 6058 is a versatile boiler water treatment product incorporating corrosion inhibitors, scale inhibitors, alkalinity builders; and amine for the control of corrosion in steam-lines.
Accepta 6058 is engineered for use in low pressure, low demand, low make-up steam boilers where it is difficult to use traditional technology and still maintain oxygen scavenger/sulphite levels due to intermittent operation or load conditions.
Accepta 6058 is available in fully recyclable plastic bottles each containing 5.5kg of concentrated solid chemical.
Accepta 6058 is packaged in cases containing 4 x 5.5kg bottles.
Each case weighs 21.8kg.
- Innovative solid chemical technology
- High performance nitrite based multi-functional treatment for low pressure steam boilers
- Excellent for low pressure, low demand, low make-up steam boilers
- Incorporates corrosion inhibitors, scale inhibitors, alkalinity builders; and amine for the control of corrosion in steam-lines
- Significant safety improvements
- Easy to handle, simple to dose
- Environmentally friendly
- Reduces carbon footprint
- Significant space savings
|Appearance:||Tan to brown amorphous solid|
|Odour:||Slight characteristic odour|
|Softening point:||49 – 55oC|
|Bulk density:||1197 kg/m3|
|Solubility in water:||Complete but dissolves slowly|
|pH (1% solution):||12.0|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
Accepta 6058 should be applied to maintain 600 – 1000 ppm nitrite in the boiler water.
Testing & Control
|Testing||In Boiler Water
||In Condensate Return|
|NO2||600 – 1000ppm||–|
|Conductivity||See manufacturers guidelines||–|
|pH||–||7.0 – 8.5|
Test kits suitable for monitoring and controlling the use of Accepta 6058 are available from Accepta.
Feed Acepta 6058 using an Acepta board system.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
For further technical assistance concerning Accepta 6058 please contact Accepta.