Accepta 6055 is a high performance, highly concentrated multi-functional solid chemical boiler water treatment product scientifically formulated for the treatment and protection of boiler systems.
Accepta 6055 is a versatile boiler water treatment product incorporating corrosion inhibitors, polymeric scale inhibitors, alkalinity builders; and a condensate corrosion inhibitor.
Accepta 6055 also contains additional sulphite making it suitable for use in systems where no de-aerator or heater is available.
All components of Accepta 6055 conform to US FDA Title 21, Section 173 Boiler Water Additives.
Accepta 6055 is available in fully recyclable plastic bottles each containing 5.5kg of concentrated solid chemical.
Accepta 6055 is packaged in cases containing 4 x 5.5kg bottles.
Each case weighs 21.8kg.
- Innovative solid chemical technology
- High performance multi-functional boiler water treatment
- Incorporates corrosion inhibitors, polymeric scale inhibitors, alkalinity builders; and a condensate corrosion inhibitor
- Suitable for systems with no de-aerator or heater
- FDA approved
- Significant safety improvements
- Easy to handle, simple to dose
- Environmentally friendly
- Reduces carbon footprint
- Significant space savings
|Odour:||Slight characteristic odour|
|Solubility in water:|
|pH (1% solution):|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
1kg of Accepta 6055, dosed at a rate of 100 ppm will treat approximately 22,000lbs of boiler blowdown.
One case of Accepta 6055 (21.8kg) is equivalent to 114kg of a conventional liquid product. Comparative values will vary, dependent upon concentration.
Testing & Control
|Testing||In Boiler Water
||In Condensate Return|
|Sulphite||20 – 30 ppm||–|
|p-Alkalinity||250 – 600 ppm||–|
|Conductivity||See manufacturers guidelines||–|
|pH||–||7.0 – 8.5|
Test kits suitable for monitoring and controlling the use of Accepta 6055 are available from Accepta.
Feed Acepta 6055 using an Acepta board system.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
For further technical assistance concerning Accepta 6055 please contact Accepta.