Accepta 6044 is a high performance, highly concentrated solid form FDA approved boiler water oxygen scavenger scientifically formulated for the treatment and protection of boiler systems from oxygen related corrosion issues.
Accepta 6044 is a solid boiler water oxygen scavenger product developed to reduce the potential for oxygen corrosion in boiler water systems.
Accepta 6044 is based on sodium sulphite and sodium lignosulphate.
All components of Accepta 6044 conform to US FDA Title 21, Section 173 Boiler Water Additives. Accepta 6044 is also an NSF approved product.
Accepta 6044 is available in fully recyclable plastic bottles each containing 5.5kg of concentrated solid chemical.
Accepta 6044 is packaged in cases containing 4 x 5.5kg bottles.
Each case weighs 21.8kg.
- Innovative solid chemical technology
- High performance boiler water oxygen scavenger
- FDA approved boiler water additives
- NSF approved
- Based on sodium sulphite and sodium lignosulphate
- Significant safety improvements
- Easy to handle, simple to dose
- Environmentally friendly
- Reduces carbon footprint
- Significant space savings
|Appearance:||Near black amorphous solid|
|Bulk density:||1197 kg/m3|
|Solubility in water:||20-25% at ambient temperatures|
|pH (1% solution):||~10.0|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
1kg of Accepta 6044, dosed at a rate of 25 ppm will treat approximately 88,000lbs of boiler blowdown. This is dependent on the levels of oxygen being removed mechanically.
One case of Accepta 6044 (21.8kg) is equivalent to 114kg of a conventional liquid product. Comparative values will vary, dependent upon concentration.
Testing & Control
|Testing||In Boiler Water|
|Sulphite||20 – 60 ppm|
Test kits suitable for monitoring and controlling the use of Accepta 6044 are available from Accepta.
Feed Accepta 6044 using an Accepta board system.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
For further technical assistance concerning Accepta 6044 please contact Accepta.