Accepta 4322 is a high performance; high molecular weight anionic latex polyacrylate based flocculant with a 20% mole charge.
Accepta 4322 is used as a flocculant for clarification, filtration and effluent systems and other processes.
Accepta 4322 is recommended for use in non-potable raw water clarification, primary and secondary effluent clarification, filtration and clarification of brine in Chlor-Soda plants where the polymer must be N free.
- High performance anionic high molecular weight latex polyacrylate
- Excellent when used as a flocculant for effluent systems and other processes
- Ideal for non-potable raw water clarification, primary and secondary effluent clarification, filtration and clarification of brine in Chlor-Soda plants
|pH:||7.0 ± 1.0 @ 5 g/1|
|Approx. bulk density:||1.05|
|Viscosity (cps):||1200 water|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
Accepta 4322 is best applied as a 0.01 – 0.05% solution.
NOTE – Do not exceed 1.0% strength otherwise viscosity rises rapidly.
The dosage details provided for Accepta 4322 are typical and can be refined by on site testing.
As a primary flocculant for settling use 1 to 5ppm.
For in line filtration use 1 to 5ppm.
For sewage treatment use 1 to 30ppm.
For oily waste water clarification use 1 to 10ppm.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.
For further technical assistance please contact Accepta.