Accepta 2016 is an excellent combined phosphate and polymer treatment for steam boiler systems up to 560 psig. Used as a scale inhibitor and suspended solids control agent it is ideal for use with softened and low hardness waters.
Accepta 2016 is a boiler feedwater treatment for scale control, achieved through a combination of a phosphate residual programme using specialist polymer technology. It can be used as a phosphate treatment at low temperatures for low harness, softened and/or de-alkalized feedwaters in boilers operating at pressures up to 40 barg.
The phosphate reacts with the hardness whilst the polymer provides transport of the Calcium, Magnesium, Iron, Phosphate and Silica through the boiler, preventing scales adhering to the metal.
- The complex phosphate reacts with calcium and magnesium, while the organic polymer provides transport of the calcium, magnesium, iron, phosphate and silica through the boiler.
- The formation of adherent deposits is prevented, thus increasing the steam production runs and reducing the danger of tube overheating.
|Flash point:||Not applicable|
|Sg:||1.09 (20.0 °C)|
|Solubility in water:||Complete|
|pH (100.0 %):||13.6|
|Viscosity:||1.4 cst (20.0 °C)|
|Pour point:||-8.3 °C|
*Full details of the product properties are available in the Safety Data Sheet. See below.
Application & Dosage Information
In low pressure steam boilers (below 20 barg) dose Accepta 2016 to generate 30 – 70ppm PO4 within the boiler water.
20 – 40 barg use 20 – 40ppm PO4 in the boiler.
40 – 60 barg use 15 – 20 ppm PO4.
Above 60 barg 10ppm.
For best results dose Accepta 2016 continuously proportional to the feedwater use.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.