Accepta 8720 is used in-conjunction with Accepta 8708 (activator) and the Activ-Ox Dosing System. Accepta 8720 is a unique product which through a controlled reaction releases the ‘active oxygen’ power of chlorine dioxide to disinfect and maintain the microbial quality of drinking, domestic and cooling water systems. It can also be used for odour control and to remove iron, manganese and sulphide from solution.
Chlorine Dioxide is an extremely effective antimicrobial agent which has significant advantages over traditional chlorine based biocides but has to be handled with extreme care because of its toxic and potentially explosive nature. Accepta 8720 is stable, easy to handle solution which when used in conjunction with the Activ-Ox Dosing System system provides all the benefits of chlorine dioxide with none of the problems.
When compared with any other means of generating chlorine dioxide the Activ-Ox system is the only system which can provide instant activation and total control.
Benefits of Chlorine Dioxide v Chlorine
|No taste or odour||Taste and odour problems|
|Does not form chlorinated by by-products||Forms trihalomethanes|
|No reaction with nitrogen containing compounds||Produces Chloramines|
|Unaffected by pH||Reduced effectiveness at high pH|
|Penetrates and disperses biofilms||Little effect on biofilms|
Application & Dosage Information
The biocidal power of Accepta 8720 only becomes available on reaction with the system activator, Accepta 8708 chlorine dioxide release agent.
Where continuous dosage is required a Activ-Ox chlorine dioxide generating system should be used.
Disinfection (dosage rates)
Accepta 8720 combined with 8708 will produce 20,000ppm which can be used as a comparison against lower strength competitor products, you would however NEVER mix the two chemicals neat. Activ-Ox chemicals are ideally combined by an Activ-Ox dosing system. For tank set ups we recommend lower strength 8710 and following the instructions carefully.
Storage tanks and domestic water services should be disinfected using 1.25L/m3 of system volume Accepta 8720 and a similar volume of Accepta 8708. The system should be left for a minimum of one hour before flushing out.
Alternatively, for large tanks spray disinfection may be employed using a solution containing 5L/m3 of Accepta 8720 and Accepta 8708.
Cooling towers and evaporative condensers should be disinfected by maintaining 25ppm of chlorine dioxide in re-circulation for a period of one hour before and after cleaning.
Accepta technical support can advise on the correct procedure.
The quality of drinking water can be maintained by continuously dosing Accepta 8720 and Accepta 8708 to provide a maximum concentration of 0.5ppm total oxidant as chlorine dioxide at outlets of the system.
Accepta technical support can advise on the correct dosage levels.
For non-drinking water applications such as domestic hot water services dosage rates may be increased to provide increased protection against Legionella Pneumophila.
Cooling towers and evaporative condensers should be dosed to maintain 0.2 to 0.5ppm chlorine dioxide in re-circulation. The residual oxidant level can be easily monitored with a simple Accepta test.
It is recommended that in all continuous dosing applications a Activ-Ox Simplicity generator system is used to ensure the correct application and maximise the benefit of this innovative product.
For further technical assistance concerning dosage rates for Accepta 8720 please contact Accepta technical support.
It is always advisable to carry out a ‘Control Of Substances Hazardous to Health’ (COSHH) assessment before use.